To send content items to your account,
please confirm that you agree to abide by our usage policies.
If this is the first time you use this feature, you will be asked to authorise Cambridge Core to connect with your account.
Find out more about sending content to .
To send content items to your Kindle, first ensure firstname.lastname@example.org
is added to your Approved Personal Document E-mail List under your Personal Document Settings
on the Manage Your Content and Devices page of your Amazon account. Then enter the ‘name’ part
of your Kindle email address below.
Find out more about sending to your Kindle.
Note you can select to send to either the @free.kindle.com or @kindle.com variations.
‘@free.kindle.com’ emails are free but can only be sent to your device when it is connected to wi-fi.
‘@kindle.com’ emails can be delivered even when you are not connected to wi-fi, but note that service fees apply.
To evaluate the effect of copper-silver ionization on Legionella colonization and nosocomial legionnaires' disease and to compare the efficacy of metal ions versus the super-heat-and-flush method of disinfection.
Prospective determination over a 36-month period of copper and silver ion concentrations in the recirculating hot-water system, Legionella colonization of the hospital water distribution system, and cases of nosocomial legionnaires' disease. Retrospective comparison of results with the previous 13 years, during which the superheat-and-flush method was used.
The Pittsburgh Veterans' Affairs Health Care System (University Drive Division) acut-care hospital.
Three copper-silver ionization systems were installed on the hot-water distribution system in November 1994.
The average number of cases of legionnaires‘ disease per year and the percentage of distal sites positive for Legionella pneumophila for the superheat-and-flush method versus the copper-silver ionization method was six cases with 15% positivity versus two cases with 4% positivity, respectively. The reduction in Legionella colonization after copper-silver ionization was significant (P<.05) compared to the superheat and flush. Mean copper and silver ion concentrations (mg/L) were 0.29 and 0.054 from hot-water tanks, and 0.17 and 0.04 from distal outlets, respectively.
We conclude that a properly maintained and monitored copper-silver ionization system was more effective than the superheat-and-flush method for reducing the recovery of Legionella from the hospital water distribution system.
Email your librarian or administrator to recommend adding this to your organisation's collection.