To save content items to your account,
please confirm that you agree to abide by our usage policies.
If this is the first time you use this feature, you will be asked to authorise Cambridge Core to connect with your account.
Find out more about saving content to .
To save content items to your Kindle, first ensure firstname.lastname@example.org
is added to your Approved Personal Document E-mail List under your Personal Document Settings
on the Manage Your Content and Devices page of your Amazon account. Then enter the ‘name’ part
of your Kindle email address below.
Find out more about saving to your Kindle.
Note you can select to save to either the @free.kindle.com or @kindle.com variations.
‘@free.kindle.com’ emails are free but can only be saved to your device when it is connected to wi-fi.
‘@kindle.com’ emails can be delivered even when you are not connected to wi-fi, but note that service fees apply.
To investigate an increase in reports of legionnaires' disease by multiple hospitals in San Antonio, Texas, and to study risk factors for nosocomial transmission of legionnaires' disease and determinants for Legionella colonization of hospital hot-water systems.
The 16 largest hospitals in the cities of San Antonio, Temple, and Austin, Texas.
Review of laboratory databases to identify patients with legionnaires' disease in the 3 years prior to the investigation and to determine the number of diagnostic tests for Legionella performed; measurement of hot-water temperature and chlorine concentration and culture of potable water for Legionella. Exact univariate calculations, Poisson regression, and linear regression were used to determine factors associated with water-system colonization and transmission of Legionella.
Twelve cases of nosocomial legionnaires' disease were identified; eight of these occurred in 1996. The rise in cases occurred shortly after physicians started requesting Legionella urinary antigen tests. Hospitals that frequently used Legionella urinary antigen tests tended to detect more cases of legionnaires' disease. Legionella was isolated from the water systems of 11 of 12 hospitals in San Antonio; the 12th had just experienced an outbreak of legionnaires' disease and had implemented control measures. Nosocomial legionellosis cases probably occurred in 5 hospitals. The number of nosocomial legionnaires' disease cases in each hospital correlated better with the proportion of water-system sites that tested positive for Legionella (P=.07) than with the concentration of Legionella bacteria in water samples (P=.23). Hospitals in municipalities where the water treatment plant used monochloramine as a residual disinfectant (n=4) and the hospital that had implemented control measures were Legionella-free. The hot-water systems of all other hospitals (n=11) were colonized with Legionella. These were all supplied with municipal drinking water that contained free chlorine as a residual disinfectant. In these contaminated hospitals, the proportion of sites testing positive was inversely correlated with free residual chlorine concentration (P=.01). In all hospitals, hot-water temperatures were too low to inhibit Legionella growth.
The increase in reporting of nosocomial legionnaires' disease was attributable to increased use of urinary antigen tests; prior cases may have gone unrecognized. Risk of legionnaires' disease in hospital patients was better predicted by the proportion of water-system sites testing positive for Legionella than by the measured concentration of Legionella bacteria. Use of monochloramine by municipalities for residual drinking water disinfection may help prevent legionnaires' disease.
To investigate a cluster of cases of legionnaires' disease among patients at a hospital.
A university hospital that is a regional transplant center.
Retrospective review of microbiology and serology data from the hospital laboratories and prospective surveillance via the radiology department; a case-control study and environmental sampling within the hospital and from nearby cooling towers.
Diagnosis of seven cases of legionnaires' disease in the first 9 months of 1996 led to recognition of a nosocomial outbreak that may have begun as early as 1979. Review of charts from 1987 through September 1996 identified 25 culture-confirmed cases of nosocomial or possibly nosocomial legionnaires' disease, including 18 in bone marrow and heart transplant patients. Twelve patients (48%) died. During the first 9 months of 1996, the attack rate was 6% among cardiac and bone marrow transplant patients. For cases that occurred before 1996, intubation was associated with increased risk for disease. High-dose corticosteroid medication was strongly associated with the risk for disease, but other immunosuppressive therapy or cancer chemotherapy was not. Several species and serogroups of Legionella were isolated from numerous sites in the hospital's potable water system. Six of seven available clinical isolates were identical and were indistinguishable from environmental isolates by pulsed-field gel electrophoresis. Initial infection control measures failed to interrupt nosocomial acquisition of infection. After extensive modifications to the water system, closely monitored repeated hyperchlorinations, and reduction of patient exposures to aerosols, transmission was interrupted. No cases have been identified since September 1996.
Legionella can colonize hospital potable water systems for long periods of time, resulting in an ongoing risk for patients, especially those who are immunocompromised. In this hospital, nosocomial transmission possibly occurred for more than 17 years and was interrupted in 1996, after a sudden increase in incidence led to its recognition. Hospitals specializing in the care of immunocompromised patients (eg, transplant centers) should prioritize surveillance for cases of legionnaires' disease. Aggressive control measures can interrupt transmission of this disease successfully.