To send content items to your account,
please confirm that you agree to abide by our usage policies.
If this is the first time you use this feature, you will be asked to authorise Cambridge Core to connect with your account.
Find out more about sending content to .
To send content items to your Kindle, first ensure firstname.lastname@example.org
is added to your Approved Personal Document E-mail List under your Personal Document Settings
on the Manage Your Content and Devices page of your Amazon account. Then enter the ‘name’ part
of your Kindle email address below.
Find out more about sending to your Kindle.
Note you can select to send to either the @free.kindle.com or @kindle.com variations.
‘@free.kindle.com’ emails are free but can only be sent to your device when it is connected to wi-fi.
‘@kindle.com’ emails can be delivered even when you are not connected to wi-fi, but note that service fees apply.
Legionella control still remains a critical issue in healthcare settings where the preferred approach to health risk assessment and management is to develop a water safety plan. We report the experience of a university hospital, where a water safety plan has been applied since 2002, and the results obtained with the application of different methods for disinfecting hot water distribution systems in order to provide guidance for the management of water risk.
The disinfection procedures included continuous chlorination with chlorine dioxide (0.4–0.6 mg/L in recirculation loops) reinforced by endpoint filtration in critical areas and a water treatment based on monochloramine (2-3 mg/L). Real-time polymerase chain reaction and a new immunoseparation and adenosine triphosphate bioluminescence analysis were applied in environmental monitoring.
After 9 years, the integrated disinfection-filtration strategy significantly reduced positive sites by 55% and the mean count by 78% (P < .05); however, the high costs and the occurrence of a chlorine-tolerant clone belonging to Legionella pneumophila ST269 prompted us to test a new disinfectant. The shift to monochloramine allowed us to eliminate planktonic Legionella and did not require additional endpoint filtration; however, nontuberculous mycobacteria were isolated more frequently as long as the monochloramine concentration was 2 mg/L; their cultivability was never regained by increasing the concentration up to 3 mg/L.
Any disinfection method needs to be adjusted/fine-tuned in individual hospitals in order to maintain satisfactory results over time, and only a locally adapted evidence-based approach allows assessment of the efficacy and disadvantages of the control measures.
Email your librarian or administrator to recommend adding this to your organisation's collection.