To send content items to your account,
please confirm that you agree to abide by our usage policies.
If this is the first time you use this feature, you will be asked to authorise Cambridge Core to connect with your account.
Find out more about sending content to .
To send content items to your Kindle, first ensure email@example.com
is added to your Approved Personal Document E-mail List under your Personal Document Settings
on the Manage Your Content and Devices page of your Amazon account. Then enter the ‘name’ part
of your Kindle email address below.
Find out more about sending to your Kindle.
Note you can select to send to either the @free.kindle.com or @kindle.com variations.
‘@free.kindle.com’ emails are free but can only be sent to your device when it is connected to wi-fi.
‘@kindle.com’ emails can be delivered even when you are not connected to wi-fi, but note that service fees apply.
To evaluate the efficacy of a new monochloramine generation system for control of Legionella in a hospital hot water distribution system
A 495-bed tertiary care hospital in Pittsburgh, Pennsylvania. The hospital has 12 floors covering approximately 78,000 m2.
The hospital hot water system was monitored for a total of 29 months, including a 5-month baseline sampling period prior to installation of the monochloramine system and 24 months of surveillance after system installation (postdisinfection period). Water samples were collected for microbiological analysis (Legionella species, Pseudomonas aeruginosa, Stenotrophomonas maltophilia, Acinetobacter species, nitrifying bacteria, heterotrophic plate count [HPC] bacteria, and nontuberculous mycobacteria). Chemical parameters monitored during the investigation included monochloramine, chlorine (free and total), nitrate, nitrite, total ammonia, copper, silver, lead, and pH.
A significant reduction in Legionella distal site positivity was observed between the pre- and postdisinfection periods, with positivity decreasing from an average of 53% (baseline) to an average of 9% after monochloramine application (P > .05). Although geometric mean HPC concentrations decreased by approximately 2 log colony-forming units per milliliter during monochloramine treatment, we did not observe significant changes in other microbial populations.
This is the first evaluation in the United States of a commercially available monochloramine system installed on a hospital hot water system for Legionella disinfection, and it demonstrated a significant reduction in Legionella colonization. Significant increases in microbial populations or other negative effects previously associated with monochloramine use in large municipal cold water systems were not observed.
Infect Control Hosp Epidemiol 2014;35(11):1356–1363
Email your librarian or administrator to recommend adding this to your organisation's collection.