To send content items to your account,
please confirm that you agree to abide by our usage policies.
If this is the first time you use this feature, you will be asked to authorise Cambridge Core to connect with your account.
Find out more about sending content to .
To send content items to your Kindle, first ensure email@example.com
is added to your Approved Personal Document E-mail List under your Personal Document Settings
on the Manage Your Content and Devices page of your Amazon account. Then enter the ‘name’ part
of your Kindle email address below.
Find out more about sending to your Kindle.
Note you can select to send to either the @free.kindle.com or @kindle.com variations.
‘@free.kindle.com’ emails are free but can only be sent to your device when it is connected to wi-fi.
‘@kindle.com’ emails can be delivered even when you are not connected to wi-fi, but note that service fees apply.
To identify the source of a pseudo-outbreak of Mycobacterium gordonae
University Hospital in Chicago, Ilinois.
Hospital patients with M. gordonae-positive clinical cultures.
An increase in isolation of M. gordonae from clinical cultures was noted immediately following the opening of a newly constructed hospital in January 2012. We reviewed medical records of patients with M. gordonae-positive cultures collected between January and December 2012 and cultured potable water specimens in new and old hospitals quantitatively for mycobacteria.
Of 30 patients with M. gordonae-positive clinical cultures, 25 (83.3%) were housed in the new hospital; of 35 positive specimens (sputum, bronchoalveolar lavage, gastric aspirate), 32 (91.4%) had potential for water contamination. M. gordonae was more common in water collected from the new vs. the old hospital [147 of 157 (93.6%) vs. 91 of 113 (80.5%), P=.001]. Median concentration of M. gordonae was higher in the samples from the new vs. the old hospital (208 vs. 48 colony-forming units (CFU)/mL; P<.001). Prevalence and concentration of M. gordonae were lower in water samples from ice and water dispensers [13 of 28 (46.4%) and 0 CFU/mL] compared with water samples from patient rooms and common areas [225 of 242 (93%) and 146 CFU/mL, P<.001].
M. gordonae was common in potable water. The pseudo-outbreak of M. gordonae was likely due to increased concentrations of M. gordonae in the potable water supply of the new hospital. A silver ion-impregnated 0.5-μm filter may have been responsible for lower concentrations of M. gordonae identified in ice/water dispenser samples. Hospitals should anticipate that construction activities may amplify the presence of waterborne nontuberculous mycobacterial contaminants.
Infect Control Hosp Epidemiol 2014;00(0): 1–6
Email your librarian or administrator to recommend adding this to your organisation's collection.